Posted 30th Nov
Been trying to put in a timed bathroom fan. Done all the work but didn’t check that I have all the correct cables in the pull cord to supply the fan. I only have permanent live and switch live. Whereas I need the addition of a neutral. So I understand it requires coming from the ceiling rose/light. Which I am a bit of a loss on how to do that. Anyhow, I am willing to admit defeat, not to mention I didn’t realise it was part P notifiable work. How much would I be looking at. I believe all the sparky needs to do is find the neutral, which is one of the two bedrooms on that loop in out lighting circuit, then connect to switch live of the pull cord. Obviously would also check I have done everything right. Which I am confident of up to supplying the fan. Is it time they charge on?